|發布時間：2019/5/25 14:20:31 瀏覽次數: 618|
在制冷工況下冷量缺乏 ，有冷風但室內不冷。 房間太大或門窗翻開，請關嚴門窗。 室內人太多或有熱源，請肅清熱源。 室外機裝置位置不佳，散熱不良，如日曬、通風不良等，請校正或重裝。 室內機位置不佳，冷氣循環差，請校正或重裝。 e. 過濾網臟堵，請清洗。 系統梗塞，檢查毛細管、過濾器、兩器等，請修復或改換。 兩器臟，請清洗。 進出風處障礙物，請肅清。|
Under refrigeration conditions, there is a lack of cooling capacity, cold air but not cold indoors. The room is too big or the doors and windows are open. Please close the doors and windows strictly. There are too many people or heat sources in the room. Please clean up the heat sources. Outdoor units are not well positioned and have poor heat dissipation, such as poor sunshine, poor ventilation, etc. Please correct or reinstall them. The position of indoor machine is not good and the air circulation is poor. Please correct or reinstall it. E. Filtration screen is dirty, please clean. System infarction, check capillary, filter, two devices, etc., please repair or change. Clean both organs, please. Obstacles in and out of the wind, please remove them.
制冷劑過多，請放出適量的制冷劑。 系統混有空氣，放氟，抽真空，重新灌注。 室外溫度太高。 查上下壓能否正常，若低壓偏高，則系統中可能會有空氣，低壓偏低，則可能制冷劑走漏、系統缺氟。 若毛細管處結霜，可能是系統中混有水份，形成冰堵，也可能是臟堵。 緊縮機自身效率低。 室外環境溫度太高?？盞髕韃拍苡邢?，不能冷到所希冀的溫馨溫度。
If there is too much refrigerant, please release a proper amount of refrigerant. The system is mixed with air, fluoride is discharged, vacuum is pumped and re-perfused. Outdoor temperature is too high. Check whether the upper and lower pressures are normal. If the low pressure is high, there may be air in the system. If the low pressure is low, there may be refrigerant leakage and fluorine deficiency in the system. If the capillary frosts, it may be mixed with water in the system, forming ice blockage, or it may be dirty blockage. Compressor itself is inefficient. Outdoor ambient temperature is too high. Air conditioners are limited and cannot be cooled to the desired warm temperature.
凝器結灰嚴重，通風不暢，散熱效果差，形成空調器制冷量降落。 空調裝置位置。室外機組受日曬；室內機組位置太高、太低、偏角，形成冷氣循環不良。 制冷循環系統梗塞。毛細管或枯燥過濾器梗塞后，流入蒸發器的液體制冷劑減少，制冷量降落。統高壓維
The condenser has serious ash condensation, poor ventilation and poor heat dissipation effect, resulting in a drop in the refrigeration capacity of the air conditioner. Position of air conditioning unit. Outdoor units are exposed to sunlight; indoor units are too high, too low, and deviation angle, resulting in poor air-conditioning circulation. Refrigeration cycle system infarction. After the capillary or dry filter is blocked, the liquid refrigerant flowing into the evaporator decreases and the refrigeration capacity decreases. Unified high-voltage dimension